2017 Hot Sale FM200 Pnuematic Filling Machine with Electrical Scale-Shineeast Brand
|FOB Price:||US $0.9 / Piece|
|Min. Order:||1 Piece|
|Min. Order||FOB Price|
|1 Piece||US $0.9/ Piece|
|Payment Terms:||L/C, T/T, Western Union|
- Model NO.: GBS-RP04-06
- Power: Pneumatic
- Performance: Filling Safely
- Trademark: SHINEEAST brand
- Specification: 700x600x1200mm
- HS Code: 8414809090
- Structure: Double Acting Booster Pump
- Application: Filling FM200 Cylinder
- Standard: Standard
- Transport Package: Safe Export Package
- Origin: Jinan, China
HFC-227ea/FM200 Pneumatic Filling Machine
Solution A: Filling machine+ Vacuum pump+ weighing system
Solution A added some sensors, electromagnetic valve, vacuump pump, and the electronic scale based on
1. Machine Composition
GBS-RP04-06-ES filling system (filling pump, precision pressure gauge, pressure reducing valve, high pressure electromagnetic valve, electric control part, etc.) and non-standard parts (weighing machine, vacuum pump)
2. Machine characteristics
GBS-RP04-06-ES filling equipment using the compressed air as power source, driving the HFC-227ea/FM200 filling and conveying, when the transmission weight reaches a certain value, the sensor signal is transferred to the gas electromagnetic valve, turn off the gas supply, pump stops working.
Then Connecting the nitrogen gas source, open the high-pressure nitrogen gas valve injection of nitrogen; when precision pressure gauge shows the needed nitrogen pressure then close the nitrogen valve; filling finished; It has the characteristics of small volume, light weight, simple operation, reliable performance. Especially suitable for the filling of heptafluoropropane in fire fighting industry.
3 .Main parameters:
|Main parameters of GBS-RP04-06-ES FM200 filling bench:|
4. Operating Procedure
1. Add lubricating oil to the FR.L Combination, the South with 10# or 20# mechanical oil, the northern winter with antifreeze mechanical oil or low condensate hydraulic oil.
2, Close the drive low-pressure gas valve, connected to the compressed air source and let pressure not more than 0.8MPa (8 bar)it.
3, Place the good empty bottle, close the HFC-227easwitch, close the high pressure nitrogen switch, open the vacuum pump switch, start the vacuum pump to vacuum.
4, When vacuum pumping is completed, close the vacuum pump pressure switch, close the unloading valve, open high pressure needle valve and low pressure gas source valve, the filling pump starts, observing the change of the weight of the electronic scale; (the set pressure is reached automatically stop working), then close the switch of HFC-227ea/FM200/Heptafluoropropane.
5, After the completion of the HFC-227ea filling, open nitrogen valve, observe valve before the pressure gauge (pressure standard table), through pressure reducing valve to the desired pressure (pressure reducing valve after the precision pressure display) by adding nitrogen to the filling bottle;
6, After the completion of the operation, close the high-pressure valve, manual valve and nitrogen valve;